Can a Greenstar Oil boiler be used with the existing conventional flue?
The conventional flue must comply with the following:
- Open (conventional) flued appliances must not be installed in or take ventilation from a bedroom, bathroom or bedsitting room
- The flue system must be in accordance with BS5410: Part 1 and the current Building Regulations
- The flue must be constructed of materials suitable for the use of condensing combustion products
- External flue systems must be of insulated type
- Brick and masonry chimneys must be lined with a suitable non-combustible material and properly jointed to withstand the effects of the working temperature (minimum rating of material 120°C) of the appliance and any condensate which may be produced
- All flue joints must be sealed to prevent the leakage of condensate and combustion products
- Ensure that joints are made so that the condensate runs away and is not collected within the joint NOTE: The flue can be increased in size from the boiler take off point providing the joint is correctly sealed. Never reduce the flue diameter from the boiler take off point.
- The flue should be vertical and contain as few bends as possible, a maximum of two 135° bends should be used
- The flue outlet must be extended beyond the eaves of the building and where possible, above the apex
- Fit a suitable anti down-draught terminal where down draughts are experienced
More All FAQs
- How many colours is the EasyControl available in?
- I can't see my website registrations in the app, what should I do?
- How do I give my engineers access?
- Does my WAI/Rewards login already work with the app?
- I don't want to use a particular feature of the app. Will this cause a problem?
- I have a great idea for the app, who do I talk to?
- What will happen at the end of my apprenticeship?
- When should I apply for an apprenticeship?
- Will any of my expenses, such as travel, be covered?
- Where will I be based?