Is an external air break required when a condensate pipe is terminated into a rainwater downspout?
When a condensate pipe is terminated into a rain water downpipe it is important that an air break is installed between the appliance condensate outlet and the drain pipe connection. The air break must be external to the property to avoid flooding (flow of rainwater into the boiler or building) should the downpipe become blocked or run full during adverse weather conditions. Failure to include an external air break may result in severe damage to the appliance and may invalidate the guarantee.
More Oil Boiler FAQs
- Top tips commissioning a Greenstar Danesmoor oil boiler
- My new Greenstar oil boiler's flue overheat thermostat keeps tripping out
- What size oil supply pipe does an oil boiler need?
- Can I use plastic pipework on oil fired sealed central heating systems?
- What ventilation do I need?
- Do you recommend treatment of the central heating water?
- How does part L of the Building Regulations affect my boiler installation?
- What can cause an oil boilers burner to lockout?
- Can I use artificially softened water in the heating circuit with my boiler?
- Can a Greenstar Oil boiler be used with the existing conventional flue?